In order for BlazeMaster to be ran exposed it must follow the listing, which states it must be installed under a smooth, flat, horizontal ceiling with quick response sprinklers. The deflector must be within 8 in. of the ceiling. Please visit the manufacturers installation instructions for the detailed instructions: https://www.lubrizol.com/CPVC/Blazemaster/Product-Information/Manufacturing-Partners.html As long as you follow […]
Questions submitted by industry professionals and answered by BlazeMaster experts.
BlazeMaster CPVC manufacturers do not certify. We do, however, offer a comprehensive, world-recognized training program that is unmatched in the industry. Our mechanical and technical excellence is demonstrated through an in-depth presentation, hands-on exercises and a final examination. Each attendee receives a training card and certificate to show inspectors on-site to demonstrate their training. We […]
If the attic requires a fire sprinkler system, BlazeMaster CPVC can be used with special sprinkler heads for this circumstance. If the attic does not require a fire sprinkler system, BlazeMaster piping can still run through to protect the floor below, but please follow the manufacturer’s listing. **Special heads that could be used in this […]
Yes, it is possible and is a very common practice. There are various fittings available with our manufacturing partners that allow you to make that transition. Please refer to NFPA section 184.108.40.206 – When nonmetallic pipe is used in combination system utilizing steel piping internally coated with corrosion inhibitors and nonmetallic piping, the steel pipe […]
BlazeMaster can be used in all high-rise occupancies as long as they are deemed as light hazard. (Hotels, apartments, offices, etc.)
The maximum diameter for BlazeMaster pipe is 3”.